BWD-01 DCA Water Decoloring Agent Water treatment Chemicals Bluwat
Description: chemical used for purification of water
- BWD-01 water decoloring agent was launch in '90s, had been
developed by BLUWAT with 20 years, stable quality, it is a new type
of high-performance decolorizing flocculant, high performance in
de-coloring, flocculating, CODcr decreasing and other applications
used to remove the color of wastewater generated by textiles
process houses and dyes industries and other fields.
- It has high color removal of dye wastewater, by providing a large
number of cations, the negative charge is brought on dye molecules
are neutralized instability, at the same time with BWD-01 Water
Decoloring Agent by a large number of hydrolysis of flocs. Can be
adsorbed dye, destabilization of the snare, from water separation,
so as to achieve the purpose of bleaching.
- The colored effluents, generated by the industries, when left
untreated, play havoc with reusable water resources. For process
houses, in water-scarce areas, it comes as heaven-sent facilitating
recycling of the industrial effluent into process water. BWD-01
Water Decoloring Agent is used to solve this problem.
- wastewater treatment in paint industry, industrial wastewater
treatment, flocculation water treatment, water clarifying agent,
water purifying agents, decolouring agent, cationic polymers water
PH Value (30% Water Solution):
Specific Gravity (at 20°C):
Completely Soluble With Water at Any Rate
30kgs net plastic drum, 250kgs net plastic drum palletized, 1250kgs
net IBC drum
High performance treating high-coloring effluent from textile
dyeing mills, pigment mills, printing ink and paper mils.
As flocculant to de-color high-colority effluent from dyestuffs
Stronger decolorization (50%~99%) and removal of COD (50%~80%).
Can ben used as retention agent in the paper & pulp processing
Faster sedimentation, better flocculation.
Non-pollution (no aluminum, chlorine, heavy metal ions etc.).
It can be used before or after biological treatment.
Less sludge produced than other inorganic coagulants.
Before use, to make BWD-01 with fresh water 40-50times, to have
2-2.5% concentration solution.
Make PAC solution with 2-5% Al2O3 content.
Make solution of Anionic flocculant with 0.1% concentration.
It is very important, to adjust the effluent pH value to 8-10,
higher or lower pH, BWD-01 works not well.
Add PAC solution, mix with effluent completely. about 1-3 minutes
Add BWD-01 solution, mix with effluent completely, about 5-10
Add small content of anionic polyelectrolyte solution, mix slowly
to have big floc. (this step is suggestion)
Check color for treated effluent
Adjust dosage of BWD-01 and PAC to do more test to have better